IDPlus and controllers are equipped with the following functions: Deep Cooling Cycle advanced algorithm that allows the quick chilling of the temperature , Easy Map function that allows multiple preloaded machine configurations and Condenser Over Heating function that allows monitoring of the compressor discharge temperature and notifying of the need for maintenance of the condenser. Controllers in the IDPlus range are new-generation devices suitable for static refrigeration units at normal and low temperatures; controllers in the IDPlus range are suitable for static and ventilated refrigeration units at low temperatures. Controllers in the IDPlus range are new-generation devices suitable for small and medium-sized mono-blocks. IDPlus controllers are equipped with the following functions: Deep Cooling Cycle advanced algorithm that allows the quick chilling of the temperature , Easy Map function that allows multiple preloaded machine configurations and Condenser Over Heating function that allows monitoring of the compressor discharge temperature and notifying of the need for maintenance of the condenser.
|Country:||Moldova, Republic of|
|Published (Last):||3 August 2013|
|PDF File Size:||7.71 Mb|
|ePub File Size:||20.3 Mb|
|Price:||Free* [*Free Regsitration Required]|
If alarms are not present, the label "SEt" appears. Access the "Machine Status" menu by pressing and quickly releasing the "set" key. The label of the "SEt" folder appears. To display the Setpoint value press the "set" key again. The value appears on the display. If alarm condition exists, when accessing The "Machine Status" menu the "AL" fold- er label appears see the "Diagnostics" section.
By pressing the "set" key when the appro- priate label appears, the value of the pro- be associated to it is displayed. To enter the folder, press "set". The label of the first visible parameter appears. To scroll through the other parameters, use the "UP" and "DOWN" keys; to change the parameter, press and release "set", then set the desired value using the "UP" and "DOWN" keys, and confirm with the "set" key to move to the next parameter.
Status ON when the compressor is started up; blinking in case of delay, protection or blocked enabling ON when defrosting; blinking in case of manual enabling ON when the alarm is enabled; blinking when the alarm is silenced ON when the fan is working PASSWORD The password allows access to program- ming parameters. In the standard configu- ration password is not present. To enable and assign it the desired value, access the "Programming" menu, within the folder with the "diS" label.
If pass- word is enabled, you will see it at the entrance of the "Programming" menu. If defrosting conditions are not present, for example the evaporator probe temperature is higher than defrost stop temperature , the display will blink three 3 times, in order to indicate that the operation will not be performed. The Copy Card is an accessory connected to the TTL serial port which allows pro- gramming quickly the instrument parame- ters.
The operation is performed as fol- lows: This command allows copy card formatting, an operation recommended in case of first use. Warning: if the copy card has been pro- grammed, using the "Fr" the data entered are erased. This operation cannot be can- celled. This operation loads the programming parameters from the instrument. This operation downloads to the instru- ment the programming parameters. The operations are performed accessing the folder identified by the "FPr" label and selecting, according to the case, "UL", "dL" or "Fr" commands; the operation is con- firmed by pressing the "set" key.
If the operation is successful an "y" is displayed, on the contrary, if it fails a "n" will be dis- played.
Downloads & Information
ELIWELL Refrigeration Controller Manuals